These indoor surface mount transfer switches are designed for fast installation in residential and commercial applications. The 18-inch flexible conduit whip attaches easily to the load center and all wires are clearly marked. Simply select the circuits needed in an emergency and connect them to the Pro/Tran wire leads.
Pro/Tran transfer switches feature a rugged powder-coated steel cabinet with six combination 1/2-inch and 3/4-inch knockouts, resettable branch rated circuit breakers and non-defeatable (break-before-make) double-throw switches. Some models feature exclusive Reliance wattmeters with accuracy of ± 3% throughout the entire range.
All models with a power inlet on the front *with exception to model 30216BRK* also include a cover for the power inlet opening that facilitates hardwiring. All models without a power inlet on the front include a covered opening that permits the installation of a power inlet for cord connection directly to the transfer switch.
A wattmeter panel (WP7500) is available for all models without meters (except models 15114A and 30114A). The wattmeter panel includes an opening, with cover, for an optional power inlet.
- Model: 31410CRK
- Model Description: Pro/Tran Kit
- Max. Generator Running Watts: 7500
- Phase: Single
- Max. Single-Pole Circuits: 10
- Max. Double-Pole Circuits: 5
- Max. Combined Load @ 125 VAC: 60
- Max. Combined Load @ 250 VAC: 30
- 15 Amp Single-Pole Circuit Breakers: 6
- 20 Amp Single-Pole Circuit Breakers: 4
- Power Inlet, NEMA: Remote
- Cord Size (gauge): 10
- Conduit Size (inches): 3/4
- Wattmeters: Yes
- Dimensions H x W x D (inches): 13.75x7x4.5
- Cabinet Type, NEMA: Indoor
- Customer Reviews
Average! Customer Rating:(7 Reviews)
7 Item(s)per page
March 28th, 2015
Comment:I bought the whole kit back in 2000. I lived within an area in Maryland that was always losing power in the winter. The installation instructions were straight forward. I didn't have any problems, and the inlet box and transfer switch worked as intended. Now that I have moved, I am buying another kit of the transfer switch and inlet box for my new house. I still have my old generator.
March 24th, 2014
Great piece of mind
Comment:Arrived quickly and very easy to install.
January 25th, 2014
Comment:Even being an old time handyman I must admit I was a little intimidated when I first looked at the install of a manual switch. Not to worry!!! This was one of the easiest installs I have done. The final product is excellent and I am very happy with my "insurance plan" should the power go out.
January 2nd, 2014
Comment:Had electrician install. Took an hour $120.00 for the install and labor. I'm ready for the big storm.
December 3rd, 2013
Comment:Order was received in 3 days. Excellent quality. Easy installation. Make sure you watch the video on YouTube prior to installing.
November 19th, 2013
Comment:Easiest to install if your box is surface mounted like shown on the installation video, however, if your box is inside the garage wall it makes the instalation more challenging. You have to cut a hole in the wall to get to the breaker box and repair the hole afterward. Howerever, after assemble the transfer box worked like advertised.
August 31st, 2011
everything you need except
Comment:Great set up, everything you need, except a length of 10-4 wire to go from the outside recepticle to the switch.
7 Item(s)per page