These indoor surface mount transfer switches are designed for fast installation in residential and commercial applications. The 18-inch flexible conduit whip attaches easily to the load center and all wires are clearly marked. Simply select the circuits needed in an emergency and connect them to the Pro/Tran wire leads.
Pro/Tran transfer switches feature a rugged powder-coated steel cabinet with six combination 1/2-inch and 3/4-inch knockouts, re-settable branch rated circuit breakers and non-defeatable (break-before-make) double-throw switches. Some models feature exclusive Reliance wattmeters with accuracy of ± 3% throughout the entire range.
All models with a power inlet on the front *with exception to model 30216BRK* also include a cover for the power inlet opening that facilitates hard-wiring. All models without a power inlet on the front include a covered opening that permits the installation of a power inlet for cord connection directly to the transfer switch.
A wattmeter panel (WP7500) is available for all models without meters (except models 15114A and 30114A). The wattmeter panel includes an opening, with cover, for an optional power inlet.
- Model: 20216A
- Model Description: Pro/Tran
- Max. Generator Running Watts: 5000
- Phase: Single
- Max. Single-Pole Ciruits: 6
- Max. Double-Pole Ciruits: 1
- Max. Combined Load @ 125 VAC: 40
- Max. Combined Load @ 250 VAC: 20
- 15 Amp Single-Pole Ciruit Breakers: 4
- 20 Amp Single-Pole Circuit Breakers: 2
- Power Inlet, NEMA: L14-20
- Recommended Cord Size (gauge): 12
- Conduit Size (inches): 3/4
- Wattmeters: Yes
- Dimensions H x W x D (inches): 7.5x7x4.5
- Cabinet Type, NEMA: Indoor
- Customer Reviews
Average! Customer Rating:(4 Reviews)
4 Item(s)per page
November 19th, 2014
Perfect solution for standby power system
Comment:The Reliance 20216A transfer switch was perfect for our application. Have had a power failure since installation, so we know everything works as it should in a real situation.
June 21st, 2014
Comment:it worked just the way it should. Easy to install.
November 18th, 2013
Great transfer switch
Comment:Installed as directed, have used on occasion for the last 6 yrs. works great, no problems.Easy to use.
November 8th, 2013
Easy and clean install
Comment:Good instructions, easy install, and it works as promised.
4 Item(s)per page